Memoria de calculo instalacion electrica residencial

Solo disponible en BuenasTareas
• Páginas : 15 (3623 palabras )
• Descarga(s) : 0
• Publicado : 2 de marzo de 2012

Vista previa del texto
INSTALACIONES ELÉCTRICAS EN BAJA TENSIÓN

PROYECTO:

CASA HABITACIÓN

PRESENTA:

JUAN ANTONIO REYES ANGELES

FECHA:

29 DE ABRIL DE 2011.

INDICE

* ANTEPROYECTO |
* NUMERO DE SALIDAS Y CARGAS |
* NUMERO DE SALIDAS Y CARGAS PARA CIRCUITOS DE OTRAS CARGAS |
* NUMERO DESALIDAS Y CARGAS PARA CIRCUITOS DE 20 A. PARA PEQUEÑOS APARATOS ELECTRICOS EN UNIDAD DE VIVIENDA |
* CALCULO DEL FACTOR DE DEMANDA |
* CALCULO DE CALIBRES PRELIMINARES |
* CALCULO DE CAIDA DE TENSION |
* CALIBRE DEL CONDUCTOR DE PUESTA A TIERRA |
* CALCULO DE LA PROTECCION PARA EL MOTOR DE LA BOMBA DE AGUA. |
*CALCULO DEL CALIBRE DE PUESTA A TIERRA. |
* CALCULO DE CANALIZACIONES |
* BIBLIOGRAFIA |
* PROYECTO FINAL. |

NUMERO DE SALIDAS Y CARGAS

No. | AREA DE OCUPACION | ARB. EXT. | ARB. INT. | PLAF. INT. | PLAF. EXT. | CONTAC. NOR. | CONTAC. F.T. | CONTAC. T.A. | MOTOR |
1 | COCHERA | | | | 3 | | 1 | | |
2 | JARDIN FRENTE | | | | 1 | | 1 | |1 |
3 | COMEDOR | | | 1 | | 3 | | | |
4 | ESTANCIA | | | 2 | | 3 | 1 | | |
5 | COCINA | | | 1 | | | 5 | | |
6 | TOILET | | | 1 | | | 1 | | |
7 | PATIO | 1 | | | | | 1 | | |
8 | HALL | | | 1 | | | | | |
9 | TERRAZA P.B. | | | 1 | | 1 | | | |
10 | BAÑO 1 | | | 1 | | | 1 | | |
11 | RECAMARA 1 | | | 1 | | 3 | | | |
12| JARDIN POSTERIOR | 1 | | | | | | | |
13 | ESCALERA | | 1 | 1 | | | | | |
14 | RECAMARA 2 | | | 1 | | 3 | | | |
15 | BAÑO 2 | | | 1 | | | 1 | | |
16 | RECAMARA 3 | | | 1 | | 3 | | | |
17 | BAÑO 3 | | | 1 | | | 1 | | |
18 | SALA DE T.V. | | | 1 | | | | 3 | |
19 | PASILLO | | | 1 | | | | | |
20 | RECAMARA 4 | | | 2 | | 4| | | |
21 | BAÑO 4 | | | 1 | | | 1 | | |
22 | RECAMARA 5 | | | 2 | | 4 | | | |
23 | BAÑO 5 | | | 1 | | | 1 | | |
24 | TERRAZA P.A. | 2 | | | | | | | |
S U M A N | 4 | 1 | 22 | 4 | 24 | 15 | 3 | 1 |

No. | AREA DE OCUPACION | 0.8 A. | 0.8 A. | 0.8 A. | 0.8 A. | 1.5 A. | 1.5 A. | 1.5A. | TOTAL(AMPERS) |
1 | COCHERA | | | | 3 | | 1 | | 3.9 |
2 | JARDIN FRENTE | | | | 1 | | 1 | | 2.3 |
3 | COMEDOR | | | 1 | | | | | 0.8 |
4 | ESTANCIA | | | 2 | | | | | 1.6 |
5 | COCINA | | | 1 | | | | | 0.8 |
6 | TOILET | | | 1 | | | 1 | | 2.3 |
7 | PATIO | 1 | | | | | | | 0.8 |
8 | HALL | | | 1 | | | | | 0.8 |
9 | TERRAZAP.B. | | | 1 | | 1 | | | 2.3 |
10 | BAÑO 1 | | | 1 | | | 1 | | 2.3 |
11 | RECAMARA 1 | | | 1 | | 3 | | | 5.3 |
12 | JARDIN POSTERIOR | 1 | | | | | | | 0.8 |
13 | ESCALERA | | 1 | 1 | | | | | 1.6 |
14 | RECAMARA 2 | | | 1 | | 3 | | | 5.3 |
15 | BAÑO 2 | | | 1 | | | 1 | | 2.3 |
16 | RECAMARA 3 | | | 1 | | 3 | | | 5.3 |
17 | BAÑO 3 | || 1 | | | 1 | | 2.3 |
18 | SALA DE T.V. | | | 1 | | | | | 0.8 |
19 | PASILLO | | | 1 | | | | | 0.8 |
20 | RECAMARA 4 | | | 2 | | 4 | | | 7.6 |
21 | BAÑO 4 | | | 1 | | | 1 | | 2.3 |
22 | RECAMARA 5 | | | 2 | | 4 | | | 7.6 |
23 | BAÑO 5 | | | 1 | | | 1 | | 2.3 |
24 | TERRAZA P.A. | 2 | | | | | | | 1.6 |
S U M A N | 3.20 | 0.80 |17.60 | 3.20 | 27.00 | 12.00 | | 63.80 |
+ 25 % | 4.00 | 1.00 | 22.00 | 4.00 | 33.75 | 15.00 | | 79.75 |

NUMERO DE SALIDAS Y CARGAS PARA CIRCUITOS DE OTRAS CARGAS

No. | AREA DE OCUPACION | 13 A. | 8.9 A. | | TOTAL(AMPERS) |
1 | COCINA (MICROHONDAS) | 1 | | | 13 |
2 | JARDIN (MOTOBOMBA) | | 1 | | 8.9 |
| | | | | |
| | | | | |
| | | | | |
| | |...