# Calculo del calor de una casa- refrigeracion y aire acondiconado

Solo disponible en BuenasTareas
• Páginas : 3 (701 palabras )
• Descarga(s) : 0
• Publicado : 8 de febrero de 2011

Vista previa del texto
INSTITUTO TECNOLOGICO DE DURANGO

DEPARTAMENTO DE METAL MECÁNICA
MANTENIMIENTO

CALCULO DEL CALOR TOTAL DE MI CASA

Profesor:

Ing. Alberto RamírezMárquez

Alumno:

Jesús Alberto Silveyra Juárez
No. Control: 05040881

Fecha: 12 de Junio de 2009

CALCULO DE QTOTAL
ESQUEMA YDIMENSIONES DE MI CASA
PARED 1
PARED 2
PARED 4
PARED 3

2.5 m

8 m
10 m

DATOS:
hint = 7 W/m2 0C
hext = 15 W/m2 0C
T1= 25 0C
T2 = 12 0C
K vidrio =0.78 W/m2 0C L vidrio = 5 mm.

El cálculo del Q total se determinará analizando cada pared de la casa

Analizando Pared 1 con 5 ventanas y 1 puerta

Vidrio
Pared
Pared

T∞ T∞R1
R0 Ri

R2
A pared con ventanas = (9X2.2) = 19.8 m2
A ventanas = (1.2 X .8 X 4) = 3.84 m + A puerta = 3.84 + (2X1) = 5.84 m2
A pared sin ventanas = 19.8 - 5.84 = 13.96 m2Rconv,int = RO = 1h As = 17wm2°C(19.8 m2) = 0.0072 °C/w
Rconv,ext = Ri = 1h As = 115wm2°C(19.8m2) = 0.0034°C/w
R1pared = Lk A = Rladrillo A = 2.31 m2°C/W13.96 m2 = 0.1655 °C/w
R2vidrio = Lk A =0.005m0.78Wm°C(5.84 m2) = .001097 °C/w
1Requ = 1R1 + 1R2 = 1.1205 + 11.097X10-3 = 919.87 w/°C
Requi = 1919.87 W/°C = 1.087 X10 -3 °C/w
RTOTAL = Ro +Requi + Ri = 5.714 x10-3°C/w + 1.087 X10 -3 °C/w +2.66 x10-3°C/w
RTOTAL = 9.467 x10 -3°C/w

Q pared 1 = T1-T2RTOTAL = 25-129.467 x10 -3°C/w = 1373.19 W

Analizando Pared 2 sin ventanas

T1T2

R0 R1 Ri

A pared = 8X2.5 = 20 m2
Rconv,int = RO = 1h As = 17wm2°C(25 m2) = 5.714 x10 -3 °C/w
R1pared = Lk A = Rladrillo A =2.31 m2°C/W20 m2 = 0.1155 °C/w
Rconv,ext = Ri = 1h As = 115wm2°C(25m2) = 2.666 x10-3°C/w
RTOTAL = Ro +R1 + Ri = 5.714 x10 -3°C/w + 0.1155 °C/W + 2.66 x10-3°C/w
RTOTAL .12388 °C/w
Q pared 2 =...