# Cuestionario

Solo disponible en BuenasTareas
• Páginas : 3 (509 palabras )
• Descarga(s) : 4
• Publicado : 24 de mayo de 2010

Vista previa del texto

TC1

TC2

CALCULO DE CALIBRE DE CONDUCTORES PRINCIPALES

CARGA TOTAL = 685.2 amp

FACTOR DE UTILIZACION

I= (0.6) (685.2) = 411.12 amp

P = 3 V I
P = 3 (220v)(411.12 amp) = 156.65 KVA

I = P / 3 V = 250kv / 3 (13.2kv) = 250 kv / 22.86 kv = 10.93amp

Ip = (10.93amp) (1.25%) = 13.66

LISTON FUSIBLE = 15amp

AJUSTE PARA LAPROTECCION DEL SECUNDARIO

I = P/ 3 V

I = 250kv / 3 (.220) = 250kv / 0.38105177 = 656.07amp

3X700

AJUSTE PARA LA PROTECCION DEL TC2

I = 99.20kv/ 3 (.220) = 99.20kv / 0.381051177 =260amp

3X300

SECCION DE BASES

S = 1000kv
V = 13.2kv

CONVERSIÓN DE IMPEDANCIAS A UNA BASE COMUN

XP.U = KVA base / KVA compañía sum.

XP.U = 1000 / 10,000 =0.01 p.u

CALCULO DE POTENCIA DE MOTORES

P = V I * n * FP / 746

I = 12 V = 220 n = 0.8 FP = 0.85

PHp = (220) (12) (0.8) (0.85) / 746 = 1795.2 / 746 = 2.40 Hp

SECADORASI = 3 V = 220 n = 0.8 FP = 0.85

PHp = (220) (3) 0.8) (0.85) / 746 = 448. 8 / 746 = 0.60 Hp

CLIMAS

I = 7.5V=220 n = 0.8 FP = 0.85

PHp = (220) (7.5) (.8) (0.85) / 746 = 1122 / 746 = 1.5Hp

IMPEDANCIA DE MOTORES

XP.U = KVA base x motor / KVA motor

XP.U = 1000 / 2.40 (.25) = 104.16 p.u

XP.U = 1000 / 0.60 (.25) = 416.6 p.u

CLIMAS

XP.U = 1000 /1.5 (.25) = 166.6 p.u

Z BASE BUS 1

Z base = (KVA real) 2 / KVA base (1000)

Z base = (13.2)2 / 1000 (1000) = 174.24

Z P.U = Z real / Z base = 0.0147 / 174.24 = 8.43X10-3

REACTANCIA/ m = 0.135

X = (0.135) (.030) = 4.05X10-3

BUS 2

Z base = (.220)2 (1000) / 1000 = 0.0484

Z P.U = 4.05X10-3 / 0.0484 = 0.083

REACTANCIA / m = 0.117

X = (0.117) (0.045) = 5.26X10-3Z P.U = 5.26X10-3 / 0.0484 = 0.10

CONTINUACION DE DE DIAGRAMA DE IMPEDANCIAS

ZT = 0.080

I P.U = 1/ Z P.U = 1 / 0.080 = 12.5 amp

I P.U = 12.5 amp

I base = KVA base / 3 V base = 1000 /...